Quick Air brand of aluminium piping is manufactured by canares engineering company for the application of compressed airline or any inert gas line, like nitrogen and argon gasses, these components are easy to modify and alter the line with short span of time. These pipe lines are of push to connect concept and pipes are of aluminium powder coated which reduce the corrosion It is available in diameter 16 to 100 mm ,quick air is having unique drops designed for moisture free air
Quickair offers a cost effective, innovative and energy efficient aluminium compressed air piping system that is very easy to assemble. Change and expand. Furthermore, labour accounts for only 20% of the cost of installing Quickair. By comparison, labour account for 60%-80% of steel system and 50%-70% of a copper system.
|Material of construction||Engineering plastic(quick air)|
|Connection type||Push to fit|
|Max.working pressure||13 bar|
|Plant testing pressure for 1 hr at 20degree c||1.5bar|
|Quality testing pressure 1 hr at 20 degree c||20 bar|
|Continuous service temp limit||80 degree c|
|Max peak temp||90 degree c (for epdm-130 d)|
|O ring & lip gasket material||HNBR/EPDM|
|Grab ring||Spring steel|
|Thread standard||BSP (Metric)|
|Fitting body surface treatment||Natural ss|
|Manufacturing with safety norms||CE|
|Size||16mm-8” quick air,15mm-54|
|Design standard||ASME B 31.1|
Before Installing Quickair system a responsible person should check the area of installation conrms to regulation designed toprevent the risk of explosion. Quickair must be installed either After the receiver or after the dryer. Flexible hose should be tted atthe beginning of the piping system. In order to counter the vibration found in any compressed air piping system. When maintaining or modifying the Quickair piping system the work must be undertaken only after the compressed air system has been vented. The installer must use only Quickair components and accessories. The installer also ensure that the installation as been properly carried out in-line with the instruction and that it meets all legal requirements.
Cutting the tubes
Champering the tubes
Losening the Caps of Fittings
Instering the tubes inside the Fittings
Tightening the assembly by Hand
Tightening the assembly by 'C' Spanner
Positioning the Droplet on the tube
Marking the position of the hole on the tube
Drilling the required hole on the tube
Champering the hole.
Aligning the Droplet to the hole.
Fixing the Droplet on the tube.
To make installation correct and safe, follow the instructions as described in the installation manual.
Join the bush with pipe.
join another pipe with bush.
Join the top and bottom clamp with the bush.
Tight the clamp with align bolts and align key.
While tightening maintain 1mm gap between top and bottom clamp.
After tightening pass the air and check the leakage with soap water